Great. So you didn't install the snmp adapter on TEC, you just let netview
receive the traps and then configed it to forward to TEC, right? Cause I think
the tecad APC install only works with the older 3.1 version of the TEC snmp
adapter. By the way do you have other traps (ie. netware, bay, cisco) being
forwarded as well? Tivoli told me that the baroc creation from running mib2trap
does not work in the NT world right now, only unix. Is that your understanding
>>> Doug Horn <Doug_Horn@HSBC.CA> 06/28 6:28 PM >>>
We have this exact setup and it works great.
We use Netview as our SNMP manager. All SNMP alerts go to it. The Netview
box runs the TEC Adapter, tecad_nv6k, to forward alerts to TEC. There are
a number of files that are needed to be configured properly to make this
happen. On the Netview side you need to configure the tecad_nv6k conf, oid
and cds files. On the TEC side you need to configure the barcoc and
possibly rules files.
When we did the APC UPS's there was a disk that gave you files that could
be added to the environment to make all the new alerts get forwarded
properly. There was an OID file which we added into the tecad_nv6k.oid
file, there was also a CDS file which we added to the existing tecad_nv6k
CDS file. We did not have to modify the tecad_nv6k.conf file.
On the TEC side we needed to add the baroc file to our TEC rule base. We
added it as its own baroc file, we did not copy it into an existing baroc
file. We then recompiled the rule base, reloaded the rule base and stopped
and restarted the TEC server.
We also installed the PowerNet Manager software on the Netview system.
This allowed Netview to discover all the APC UPS's on the network, run
PowerNet from a pull down menu, etc.
Using PowerNet we could get an APC UPS to run a self test, this would cause
it to send an SNMP alert which would show up in TEC.
The bottom line is that APC gives you the config file additions you require
so that you do not have to create them yourself. This is nice because I
think there are almost 100 SNMP alerts the UPS will generate and when you
type like me this would take for ever.
On Mon, Jun 28, 1999 at 09:54:22AM -0400, Todd E. Lewis wrote:
> So I'm sort of back to where I was. From what I understand there is
> no current way to forward these traps from netview (ie.. APC, Netware
> etc..) because NT does not at the moment support baroc configurations
> to TEC. Is that your understanding as well?
I'm not familiar with NT not supporting baroc config. If it is indeed
a problem, then a possible temp work around would be to install the
TEC SNMP adapter to receive UPS traps & have the TEC SNMP adapter
on forward those events to TEC. What this simply means is that you now
have most of your events forwarded to TEC by Netview while TEC SNMP
adapter is forwarding UPS traps. A possible alternative.
> >>> YEO Khee Seng <yeoks@RALEIGH.IBM.COM> 06/28 9:43 AM >>>
> On Mon, Jun 28, 1999 at 07:58:36AM -0400, Todd E. Lewis wrote:
> > I've got a pmr open, and the tech tells me I should install it on TEC
> > to be able to receive traps from our ups's which has a rule base
> > on TEC. I'm alittle confused because I've thought all along that the
> > Netview server should act as the main snmp manager.
> TEC SNMP adapter is targetted at customer that do not have SNMP manager
> in place (ie no Netview, Openview, etc). So for people with no Netview
> installed, the UPS traps (as in your example) would have to be forwarded
> to the box with the TEC SNMP Adapter.
> > >>> James Shanks <James_Shanks@TIVOLI.COM> 06/25 6:50 PM >>>
> > A TEC adapter is a piece of code which ships events to TEC in a
> > undertands. The TEC server is about the only place you probably would
> > install a TEC adapter. You can run the TEC SNMP adapter in the same
> > NetView, though few people do. It was originally designed by TEC to
> > boxes which had no SNMP manager to report to.
> > James Shanks
> > Tivoli (NetView for UNIX) L3 Support
> > "Todd E. Lewis" <telewis@PROVBANK.COM> on 06/25/99 02:21:01 PM
> > Please respond to Discussion of IBM NetView and POLYCENTER Manager on
> > <NV-L@UCSBVM.UCSB.EDU>
> > To: NV-L@UCSBVM.UCSB.EDU
> > cc: (bcc: James Shanks/Tivoli Systems)
> > Subject: Netview/SNMP
> > I'm alittle confused, Can the TEC SNMP adapter be installed on the
> > server to forward snmp events to TEC or does it get installed on TEC?
YEO Khee Seng firstname.lastname@example.org
The opinions expressed are my own and do not reflect those of IBM.